Federal Aboveground Storage Tank Process (18-FD-b)
Note, that a developer may also have to comply with state permitting and compliance regulations.
Aboveground Storage Tank Process Process
18-FD-b.1 – Does the Aboveground Storage Tank Require an SPCC Plan under 40 CFR 112.1?
Non-transportation related onshore and offshore facilities drilling, producing, gathering, storing, processing, refining, transferring, distributing, using, or consuming oil or oil productions with oil in above ground storage tanks which could discharge in quantities that may be harmful to navigable waters of the United States or adjoining shorelines are subject to 40 CFR § 112.1 and the completion of an SPCC Plan unless excluded. Among the exclusions to the SPCC Plan requirement are facilities not subject to EPA jurisdiction as well as facilities with both a completely buried storage capacity of 42,000 gallons or less (excluding containers "permanently closed”) and aggregate aboveground storage capacity of 1,320 gallons or less (excluding containers with a capacity under 55 gallons and containers “permanently closed”). 40 CFR § 112.1(d)(2)
18-FD-b.2 to 18-FD-b.3 – Does the Regional Administrator Make a Preliminary Determination Requiring the Developer to Prepare an SPCC Plan?
An EPA Regional Administrator may require the developer of any facility subject to EPA regulation under CWA 311(j), regardless of the above listed exclusions, prepare an SPCC Plan, or any applicable part thereof, to carry out the purposes of the SPCC.
18-FD-b.4 – Notice of Preliminary Determination to Require an SPCC Plan
Following a preliminary determination by the Regional Administrator to require an SPCC Plan, the Regional Administrator must provide written notice to developer stating the reasons why the developer must prepare an SPCC Plan, or applicable part thereof.
18-FD-b.5 – Provide Data and Consult with EPA
The developer may provide information and data as well as consult with the EPA about the requirement to prepare an SPCC Plan for 30 days after receiving the written notice. 40 CFR § 112.1(f)(2)
18-FD-b.6 – Does the Regional Administrator Make a Final Determination Requiring the Developer to Prepare an SPCC Plan?
The Regional Administrator must make a final determination of whether to require an SPCC Plan after the 30 days in which the developer may provide data and consult with the EPA on the SPCC Plan. 40 CFR § 112.1(f)(2). If the Regional Administrator makes a final determination that an SPCC Plan is necessary, the developer must prepare the plan within six months of the final determination and implement the plan not later than one year after the final determination. 40 CFR § 112.1(f)(4).
18-FD-b.7 – Spill Prevention, Control, and Contingency (SPCC) Plan
The developer must prepare a Spill Prevention, Control, and Contingency Plan (SPCC). Under 40 CFR § 112.7 the SPCC Plan must include:
- a description of the physical layout of the facility;
- the type of oil in each container and its storage capacity;
- discharge prevention measures, including procedures for routine handling of products;
- discharge or drainage controls;
- countermeasures for discharge discovery, response, and cleanup;
- methods of disposal of recovered materials in accordance with applicable legal requirements;
- a contact list and phone numbers for the facility response coordinator, National Response Center, cleanup contractors, and all appropriate Federal, State, and local agencies who must be contacted in case of a discharge.
40 CFR § 112.7(a)(3). Additionally, unless the facility also requires a Response Plan under 40 CFR § 112.20, the SPCC Plan must include information and procedures to enable a person reporting a discharge to relate information on the:
- address, location, and phone number of the facility;
- the date and time of the discharge;
- the type of material discharged;
- estimates of the quantity discharged;
- the source of the discharge;
- a description of all affected media;
- any damages or injuries caused by the discharge;
- actions being used to stop, remove, and mitigate the effects of the discharge;
- whether an evacuation may be needed; and
- the names of individuals and/or organizations who have been contacted.
Feedback | Add a Contact