FERC Order No. 792
Legal Document- RegulationRegulation: FERC Order No. 792Legal
FERC Order No. 792, current through June, 3, 2013. FERC Order No. 792 amends the pro forma Small Generator Interconnection Procedures and pro forma Small Generator Interconnection Agreement to: (1) incorporate provisions that provide an Interconnection Customer with the option of requesting from the Transmission Provider a pre-application report providing existing information about system conditions at a possible Point of Interconnection; (2) revise the 2 megawatt (MW) threshold for participation in the Fast Track Process included in section 2 of the pro forma SGIP; (3) revise the customer options meeting and the supplemental review following failure of the Fast Track screens so that the supplemental review is performed at the discretion of the Interconnection Customer and includes minimum load and other screens to determine if a Small Generating Facility may be interconnected safely and reliably; (4) revise the pro forma SGIP Facilities Study Agreement to allow the Interconnection Customer the opportunity to provide written comments to the Transmission Provider on the upgrades required for interconnection; (5) revise the pro forma SGIP and the pro forma SGIA to specifically include energy storage devices; and (6) clarify certain sections of the pro forma SGIP and the pro forma SGIA. The reforms should ensure interconnection time and costs for Interconnection Customers and Transmission Providers are just and reasonable and help remedy unduediscrimination, while continuing to ensure safety and reliability.
- Year Signed or Took Effect
- Legal Citation
- 145 FERC ¶ 61,159
- Not Provided
Check for DOI availability: http://crossref.org
- Internet link for FERC Order No. 792
FERC Order No. 792 (2013).